Payment & Shipping Terms:
|Material:||Alloy Steel||Standard:||ASTM A335|
round steel tubing,
steel tube pipe
Seamless Ferritic Alloy Steel Pipe ASTM A335 P5 Pipe for Power Plant
Specialized in providing various steel pipes for more than 10 years, TIPTOP offers ASTM A335 P5 seamless large caliber & heavy wall thickness pipe with competitive price, premium quality and flexible delivery time. Third party inspection is available.
For the low and medium pressure boiler and steam header pipes;
For the high-pressure boiler and steam pipes, and the petrochemical industry pipes;
Power plant; Chemical Fertilizer; Petrochemicals; Offshore Oils; Gas Productions; Refineries and etc.
2. Available Size Range
|*If the steel grades and size you are looking for are not listed above, please contact us for further information.|
ASTM A335 Standard Specification for Seamless Ferritic Alloy-Steel Pipe for High-Temperature Service
4. Ordering Information
Quantity (feet, meters, or number of lengths),
Name of material (seamless alloy steel pipe),
Manufacture (hot-finished or cold-drawn),
Size using one of the following:
NPS and schedule number;
Outside diameter and nominal wall thickness;
Outsider diameter and minimum wall thickness;
Inside diameter and nominal wall thickness;
Inside Diameter and minimum wall thickness.
Length (specific or random)
End finish (plain end or bevel end)
5. Chemical Requirements
6. Tensile Requirements
Tensile Strength min.: 60ksi / 415MPa
Yield Strength min.: 30ks / 205MPa
7. Inspection & Test
Chemical composition, mechanical properties ( tensile strength, yield strength, elongation, flaring, flattening, bending, hardness, impact test), surface and dimension, NDE, hydrostatic test.
Hot Rolled or Cold Drawn
9. Manufacturing Process
Raw Material Inspection → Cold Centering → Heating → Piercing & Rolling → SIzing → Heat Treatment → Testing → Finishing → NDE → Visual & Dimension Inspection → Marking → Storing & Shipping
10. Supplementary Requirements
S1. Product Analysis
Product analysis shall be made on each length of pipe. Individual lengths failing to conform to the chemical composition requirements shall be rejected.
S2. Transverse Tension Tests
A transverse tesnion test shall be made on a specimen from one end or both ends of each pipe NPS 8 and over. If this supplementary requirement is specified, the number of tests per pipe shall also be specified. If a specimen from any length fails to meet the required tensile properties (tensile, yield, and elongation), that length shall be rejected subject to retreatment in accordance with Specification A999/A999M and satisfactory retest.
S3. Flattening Test
S4. Metal Structure and Etching Tests
The steel shall be homogeneous as shown by etching tests conducted in accordance with the appropriate portions of Method E381. Etching tests shall be made on a cross section from one end or both ends of each pipe and shall show sound and resonably uniform material free from injurious laminations, cracks, and similar objectionable defects. If this supplementary requirement is specified, the number of tests per pipe required shall also be specified. If a specimen from any length shows objectionable defects, the length shall be rejected, subject to removal of the defective end and subsequent retests indicating the remainder of the length to be sound and resonably uniform material
S6. Photomicrographs for Individual Pieces
S7. Alternative Heat Treatment -Grade P91
S8. Melting Practice - Grades P2 and P12
Contact Person: zaya_z