Payment & Shipping Terms:
|Material:||Carbon Steel||Standard:||ASTM A106|
round steel tubing,
steel tube pipe
Power Plant Seamless Steel Pipe ASTM A106 Gr. B for High Temperature Service
ASTM A106 Grade B pipe is one of the most popular seamless steel pipes applied in different industries. Not only in pipeline systems like oil and gas, water, mineral slurry transmission, but also for boiler, construction, structural purposes.
1. Available Size Range
|*If the steel grades and size you are looking for are not listed above, please contact us for further information.|
ASTM A106 Standard Specification for Seamless Carbon Steel Pipe for High-Temperature Service
Oil, Gas and water delivery;
Refinery, Boiler and Mechanical equipment manufacture;
Structure construction; drilling, ship building and etc.
4. Ordering Information
Quantity (feet, meters, or number of lengths),
Name of material (seamless carbon steel pipe),
Grade (Grade B),
Manufacture (hot-finished or cold-drawn),
Size (NPS/DN and weight class or schedule number, or both; outside diameter and nominal wall thickness; or inside diameter and nominal wall thickness),
Special outside diameter tolerance pipe,
Inside diameter tolerance pipe, over 10 in, (250mm) ID.
Length (specific or random),
Test report required,
5. Chemical Requirements
A For each reduction of 0.01% below the specified carbon maximum, an increase of 0.06% manganese above the specified maximum will be permitted up to a maximum of 1.35%.
B Unless otherwise specified by the purchaser, for each reduction of 0.01% below the specified carbon maximum, an increase of 0.06% manganese above the specified maximum will be permitted up to a maximum of 1.65%.
C These five elements combined shall not exceed 1%.
6. Mechanical Properties
Tensile Strength, min: 60ksi/415MPa
Yield Strength, min: 35ksi/240MPa
7. Manufacturing Process
Raw Material Inspection → Cold Centering → Heating → Piercing & Rolling → SIzing → Heat Treatment → Testing → Finishing → NDE → Visual & Dimension Inspection → Marking → Storing & Shipping
8. Heat Treatment
Hot-finished pipe need not be heat treated. Cold-drawn pipe shall be heat treated after the final cold draw pass at a temperature of 1200°F(650°C) or higher.
9. Supplementary Requirements
S1 Product Analysis
S2 Transverse Tension Test
S3 Flattening Test, Standard
S4 Flattening Test, Enhanced
S5 Metal Structure and Etching Test
The steel shall be homogeneous as shown by etching tests conducted in accordance with the appropriate sections of method E381. Etching tests shall be made on a cross section from one end or both ends of each pipe and shall show sound and reasonably uniform material free from injurious laminations, cracks, and similar objectionable defects, the length shall be rejected, subject to removal of the defective end and subsequent retests indicating the remainder of the length to be sound and resonably uniform material.
S6 Carbon Equivalent
S7 Heat Treated Test Specimens
S8 Internal Cleanliness-Government Orders
S9 Requirements for Carbon Steel Pipe for Hydrofluoric Acid Alkylation Service
Contact Person: zaya_z